Freezer installation complications
NSW Service Manager Ben Denyer had to deal with this ice up Easter Monday. Disappointingly the installer (not Tecair) caused the freezer installation complications.
The freezer room was not fitted with a liquid line solenoid, there is no pump down before defrost. The defrost termination probe was jammed in the back of the coil close to the heater. No CPR valve has been fitted to limit the compressor current after defrost.
This evap is only 3 years old and is now a complete write off due to the ice damage caused from incorrectly located defrost termination probe and no pump down before defrost.
Drain is run in 20mm electrical conduit with electrical junction boxes in place of Tees. Just a poor finish in general.
» View Tecair’s commercial refrigeration services.